Operation Method of Sodium Hypochlorite And Backwash
Electrolysis of sodium hypochlorite before operation, we need to connect the power supply, and then combine industrial salt dissolved sodium chloride in the device, and then open the device through filtering valve will salt water precipitation into the storage box of the sodium chloride solution, then, start from the water distribution switch, equipment automatically hook with salt water to dilute brine concentration is approximately 3.5%; Then open the valve to adjust the flow meter, and let the mixed brine flow through a set of interlayer electrolyzer composed of a group of anode and cathode tubes at the set flow rate. Finally, start the rectifier current switch, and open the cooling water valve to cool the electrolyzer at the same time, so that the equipment starts to work normally.
What is the backwash operation of the sodium hypochlorite?
After each shift of operation of sodium hypochlorite, it must be backwashed once. In backwashing, the vent valve should be opened first to drain the salt water in the pipe, then the reverse flushing vent and the inlet valve should be opened to flush for about 10 minutes, and then the vent valve should be opened to drain the water for use next time.
Pickling: it needs to be pickling when it runs up to 250 hours, according to water conditions corresponding to extend or shorten the cycle of pickling, pickling, the first open all emptying valve, the pipeline of the stockpile brine drained, and then open the into acid and acid valves, valve until the vent pipe pipe outflow organic acid water, shut down into acid valve, with acid water soak in the electrode tube dropped the acid water again after 1-2 hours, then backwash time, usually allocate concentration about 10% in dilute hydrochloric acid.
Milestone Chlorination technologies co. LTD specializes in sodium hypochlorite, chlorine dioxide generator, the integration of production and application of sewage treatment equipment, especially the sales lead SYDC type combined sodium hypochlorite, is my company summarizes domestic and foreign existing equipment and technical characteristics, complement each other, carefully study and become a simple small combined chlorine agent preparation device, is used widely cheap industrial salt sea water or dilute solution by generating diaphragm electrolysis device for sodium hypochlorite solution. This device is mainly used for disinfection of hospital sewage, drinking water and sewage, and also for disinfection of food utensils, vegetables and fruits. The company's product users all over the country more than 20 provinces, municipalities directly under the central government, autonomous regions, in many cities across the country with agents, established a large sales and after-sales service network.
May 21, 2019The functions that swimming pool chlorination systems are supposed to have: During the operation of the swimming pool chlorination systems, a large amount of hydrogen is generated on the plate.view