Basic Operating Procedure of Hypochlorite Generator Sea Water
When it's working, firstly switch on the power supply, hypochlorite generator sea water will add ordinary industrial salt (0.35 yuan per kg) into the desalination device and dissolve it into about 10% salt water, open the valve and let the salt water enter the salt liquid storage tank through filtration and precipitation. Then, we turn on the water distribution switch, the equipment automatically mix salt water to the concentration of about 3.5% of the dilute salt water; Then open the valve to adjust the flow meter, and let the mixed brine flow through a set of interlayer electrolytic cell composed of a group of anode and cathode tubes. Finally, the sodium hypochlorite generator starts the rectification current switch and opens the cooling water valve to cool the electrolyzer. The sodium hypochlorite generator starts to work. In this way, the whole equipment produced the standard hypochlorite generator sea water(concentration of about 1%); Finally, the liquid medicine automatically flows into the liquid medicine storage tank, which is convenient for storage and backup at any time.
Backwash: after each shift is completed, backwash must be done once. During the backwash, open the vent valve first to drain the brine in the pipe, then open the backwash vent and backwash the inlet water valve for about 10 minutes, and then open the vent valve to drain the water for use next time.
Pickling: hypochlorite generator sea water usually run 250 hours to pickling time, according to water conditions corresponding to extend or shorten the cycle of pickling, pickling, the first open all emptying valve, the pipeline of the stockpile brine drained, and then open the into acid and acid valves, valve until the vent pipe pipe outflow organic acid water, shut down into acid valve, with acid water soak in the electrode tube dropped the acid water again after 1-2 hours, then backwash one more time, usually allocate concentration is about 10% in dilute hydrochloric acid.
March 8, 2019Chlorine dioxide generation system is widely used in various domestic water places, restaurants, hospitals, hotels, factories and other industries that need to be disinfected and sterilized.view